GonLED is proud to announce a successful energy efficient lighting retrofit at USAG Yongsan. The lighting retrofits will provide USAG Yongsan with energy savings greater than 40% while improving the quality of the lighting. These quality improvements include quiet operation, improved color rendering, and a reduction in HVAC costs due to less heat being generated by the lighting system.
4-Lamp F34T12 Lamps and magnetic ballast
Power consumption: 148 Watts
4-Lamp F25T8 Energy Saving Lamp with High Efficiency ballast
Power consumption: 84 Watts – 64 Watt savings (43% reduction)
Light Level: Increase by 3% to 12% depending on lamp used
Energy Savings Equals Dollars
Based upon the annual operating hours and utility rate, the energy savings can be used to calculate the operating cost savings:
|Annual Operating Hours:||4,000|
|Utility rate ($/Kwh):||x $0.08|
|Energy Savings per fixture (Watts):||x 64|
|Conversion from W to KW:||÷ 1,000|
|Annual Cost savings per fixture:||$20.48|
Multiply this value by the number of fixtures in the garrison to determine the total cost savings:$20.48 x 30,000 (fixtures) = $614,400
For more information please contact a GonLED customer representative.